Electric heated air curtains with ½ HP motors are normally used over customer entrance doorways in restaurants, supermarkets, department stores, personnel entrances, etc. and installed no more than 8’ above the floor. The colder the climate the higher the kW heater should be selected. If specifying electric heated models for use over warehouse doorways, use either HV or EP models. Higher kWs should be used in this case. Most electric heated models are supplied with motor control panels and wall mounted thermostats for ON/OFF/Fan Only control.
Air Curtain FAQ & Troubleshooting Guide
Mounting & Installation
Units should be mounted next to each other; however, if the door opening is wider than the units, spacing up to 6” between units is acceptable. LPV25 models can be spaced up to 3” apart. For wider pass-thru openings, use the LoPro series.
Whenever possible, avoid using an air curtain that is shorter than the entire width of the door opening. An undersized air curtain will create unprotected areas on each side, thereby reducing its efficiency level. An air curtain should cover the doorway completely. If necessary, it’s always better to use an air curtain that is slightly wider, than shorter, in covering the opening. Some manufacturers will provide their units with extreme side deflectors to help spread the air outward. Avoid using this type of design. The output airflow pattern becomes very irregular. Much of the airflow moves across the opening, causing considerable air velocity loss by the time it hits the floor.
When installation is not possible over the top of the doorway some Mars Air Curtains may be vertically mounted on either side of the door, blowing across the door opening; this type of installation must be specified at time of order. The pan of the motor/fan assembly will be bolted to the air curtain housing instead of the standard wing nut mount hardware. All motors used in Mars Air Curtains contain thrust bearings and operate efficiently in any position.
Each motor within the air curtain housing will have one watertight junction box mounted internally. Contact factory for specific location. If specified at time of order, the junction box can be located elsewhere.
Mars provides a variety of optional mounting hardware accessories. Side extension plates are available to further extend the outboard mounting hole on the STD, HV, and EP models when being used to clear existing lines and tracks over a doorway. These plates are available in various sizes up to a 9” extension for both ends of the air curtain. Adjustable mounting brackets and extended wall mount brackets for drum type roll-up doors are also available; these types of brackets are used when the air curtain needs to be mounted some distances away from the wall. The brackets are available in various sizes to provide 2 ½” to 23” of clearance. Please consult factory for details.
Operation & Performance
Yes, as long as the air curtain is mounted on the outside of the oven and operating temperature does not exceed 120° F. The smaller the opening, the more effective the installation as the percent of heat loss is held to a minimum.
Yes, use the same models as you would over a regular freezer.
The air leaves the discharge nozzle at very high velocities. The air spread and depth of "air wall" created varies between models. A general rule of thumb is: for units with 1HP motor(s) or less, the air spread is up to 3” and the depth of the wall of air created is about 18”, measured 6’ from the nozzle. For units with motor(s) larger than 1HP, the air spread is up to 6” and the depth of the wall of air is about 24”, measured 6’ from the nozzle.
All motors have lifetime lubricated sealed ball bearings, making greasing or oiling unnecessary. Blowing or wiping dust off the fans and motors whenever it is visible is advisable to ensure maximum performance.