To be most effective, the air curtain should be mounted inside the foyer over the building entrance door. Depending upon climatic conditions, either a heated or unheated model may be used.
Air Curtain FAQ & Troubleshooting Guide
Mounting & Installation
No. Air curtains provide up to an 80% thermal efficiency level. The continual loss of refrigerated air and build-up of humidity within the cooler will cause the compressor to burnout. Air Curtains are meant to be used as an energy saving device when the cooler door needs to be opened for loading and unloading purposes.
Mars provides a variety of optional mounting hardware accessories. Side extension plates are available to further extend the outboard mounting holes on the STD, HV, and EP models. These plates are available in various sizes up to a 9” extension for both ends of the air curtain. Adjustable mounting brackets and extended wall mount brackets for drum type roll-up doors are also available. These types of brackets are used when the air curtain needs to be mounted some distances away from the wall. The brackets are available in various sizes to provide 2 ½” to 23” of clearance. Please consult factory for details.
Sometimes one unit can be installed over the door opening on top of the track, but very often there are obstructions and the unit would have to be installed much too high. Therefore, one unit on each side of the track would be more efficient because installation is then closer to the top of the door opening. The air curtain should be mounted 3” to 4” away from each side of the track to prevent interference with products being sent through.
The average time required to install a unit is two hours. After the second or third installation, the time can usually be cut to one hour.
No, they are not normally required as their design protects them from inclement weather. Weatherproof covers may be recommended when the units are exposed to harsh environments or excessive moisture. All unheated units are ETL/UL listed for outdoor use.
Yes, if the level of sound is a problem mount the air curtain outside and the sound will be reduced.
Mount air curtain ½” to 2” above the door opening whenever possible. The closer to the top of the door opening, the more effective the air curtain will be. Extended mounting brackets are available in various lengths so the air curtain can be mounted to clear an obstruction. If the unit is mounted higher, move it 3/8’’ away from the wall for every 1’’ it is moved above the door.
Not more than 8” for refrigeration and 14” for insects. To seal off the ends, 12” to 18” panels made of sheet metal, plastic strips, or plywood can be installed on each side of the door opening to improve the efficiency of the air curtain. Sometimes the Mars Air Curtain outlet nozzle may be installed between the obstruction and the wall. Precaution is necessary to prevent the obstruction from deflecting the flow of air.